Fire Alarm Systems
Cease Fire & Electrical Services gives complete services of Fire Alarm Systems from installation, testing, commissioning and maintenance last 25 years.
We are recognized Fire Alarm Systems supplier and trader in Mumbai – Maharashtra – India.
We are an established of the industry engaged in trading and supplying a finest range Conventional Fire Alarm System, Addressable Fire Alarm System. Offered products are precision engineered by making use of technologies and tools in compliance with industry laid parameters.
Our fire alarm system has a number of devices working together to detect and warn people through visual and audio appliances when smoke, fire, carbon monoxide or other emergencies are present. These alarms may be activated automatically from smoke detectors, and heat detectors or may also be activated via manual fire alarm activation devices such as manual call points or pull stations. Alarms can be either motorized bells or wall mountable sounders or horns. They can also be speaker strobes which sound an alarm, followed by a voice evacuation message which warns people inside the building not to use the elevators. Fire alarm sounders can be set to certain frequencies and different tones including low, medium and high.
Fire Alarm Control Panel (FACP) Functional Description The fire alarm control panel (FACP) shall be the central processing unit of the system, receiving and analysing signals from fire sensors, providing audible and visual information to the user, initiating automatic alarm response sequences and providing the means by which the user interacts with the system. The FACP shall be certified as meeting the requirements of EN54-2 and EN54-4 by a suitable, notified body. A certificate and test report shall be made available for inspection as evidence of certification. The FACP shall be easily configurable to meet the exact detection zone and output mapping requirements of the building. The FACP shall be microprocessor based and operate under a multitasking software program. Operating programs and configuration data shall be contained in re-configurable non-volatile memory. Retention of the memory shall not rely on any form of battery or capacitor back-up device. The FACP shall incorporate separate processors for loop processing and central processing. Up to 240 individually addressed standard devices shall be configured on each addressable loop. Loop powered sounders and beacons incorporated as sensor bases shall be available. The FACP shall have the capability to support sub-addressing of addressable modules.It shall be possible to fit a 40-column printer to the FACP which will print system events automatically and logged data upon request. The FACP shall incorporate a real time clock to enable events to be referenced against time and date.
Returns Policy: Once goods sold will not be taken back.
For more information go through our website http://www.ceasefireservices.com or call / mail us.
We provide these Fire Alarm Systems services all across India in cities like
Mumbai (Dadar, Bandra, Andheri, Borivilli, Palghar, Churchgate, Fort, Vasai, Sion, Chembur, Kalyan, kurla, Virar, Belapur, Ghatkopar), Navi Mumbai, Vashi, Thane, Shirdi, Vapi, Lonavala, Lavasa, Matheran, Mahabaleshwar, Nagpur, Aurangabad, Solapur, Kolhapur, Surat, Pune, Ahmedabad, Nashik, Ratnagiri, Bengaluru, Hyderabad, Baroda, Goa.